Biogas dehumidification system
For the DRYPACK PLUS version, each component is designed according to its typology.
- The DRYPACK ONE and FLEX systems are not designed to be installed in an ATEX zone. - Damage is possible if installed in harmful atmospheres or in the presence of H2S or NH3. These atmospheres may be present in landfills or WWTW (waste water treatment works) in particular. If there is a high concentration of H2S, it is recommended that adequate preventive measures are taken. - For further information, please contact your CIAT representative. INSTALLATION - DRYPACK ONE and FLEX systems must be installed outdoors, in a ventilated area. - Any air intakes must be more than 5 m from the DRYPACK system. - Ensure there is sufficient free space around the device to facilitate service operations. To ensure easy cleaning of the tubes, we recommend a removable box is fitted perpendicular to the cooler axis (not provided). - A safety zone where only authorised personnel are allowed to enter must be set up around the unit. - The biogas circuit connections must be ISO PN10 - 01A NFEN 1092-1 type flanges with a tanged metal reinforced graphite gasket.
Biogas circuit By-pass for maintenance (recommended) Elements not provided: : Removable box (recommended) : Coupling for inerting (recommended) : Mist eliminator filter (recommended for landfill gas or WWTW) : Shut-off valves (mandatory)
Biogas connections using ISO PN10 - 01A NFEN 1092-1 flanges and tanged metal reinforced graphite gasket
Coupling for inerting (standard equipment)
HEAT PUMPS - AIR CONDITIONING - REFRIGERATION - AIR HANDLING - HEAT EXCHANGE - NA 17.01 A
DPO 015 168-20C H05L DPO: DRYPACK version: DPO (DRYPACK ONE) or DPF (DRYPACK FLEX) 015: chiller size 168: cooler diameter (mm) 20: cooler length (dm)
C: cooler tubes: L = smooth, C = corrugated H05L: Economiser (E) or Heater (H) option. 0000 if option not selected 05: length of the economiser or heater (dm) L: economiser or heater tubes: L = smooth, C = corrugated