1060 1080 1100 1120 1140 1160 1180
Up to size 1180, these units can be transported by container.
If speed regulators other than those recommended by the manufacturer are used, check that these are compatible with the electric motors. Commissioning and maintenance: refer to the instruction manual. These units comply with the European directives. The installer is responsible for ensuring the compliance of the installation. The installer must ensure safety and protective devices (emergency stop, shut-off valves, lightning protection, etc.) are put in place and are accessible.
These units are designed to operate outside. When starting up, frost and snow could adversely impair its operation. As a general measure, all steps should be taken to avoid the risk of air recycling. This is especially important when the installation comprises several units. It is not recommended to install units near the hot air extraction duct outlet or close to deciduous plants (this could cause clogging). Allow a clearance of 1.5 m around the device. Where the use of antivibration mounts is required, use a rigid frame which locks the feet together.
HEAT PUMPS - AIR CONDITIONING - REFRIGERATION - AIR HANDLING - HEAT EXCHANGE - NA 17.01 A